## How can I use sprinkler K factor information in Pipe Flow Expert?

Pipe Flow Expert allows the modelling of a sprinkler through the generic Component object, through the definition of the performance characteristic, either by specifying a Sprinkler K factor, or by specifying a set of flow rate versus pressure-loss performance points.

The following discussion explains how Sprinkler K factors relate to flow versus pressure loss performance data.

PRESSURE LOSSES for SPRINKLERS

Many sprinklers are rated with a K factor that describes their performance. This is defined as:

Q = K √(P)

Where: Q = Flow rate (US gpm or l/min, K has units of US gpm/psi0.5 or l/min/(bar)0.5 depending on the published literature.

The K factor for sprinklers is NOT the same as a fitting K factor (which is used with a velocity2 element to calculate head loss).

Typical sprinkler Discharge Coefficients might be:

K=5.6 (where the units are in US gpm/psi0.5)
This equates to a metric K of 80.6 (units are in (l/min)/bar0.5)

or
K=8.0 (where the units are in US gpm/psi0.5)
which equates to a metric K of 115.2 (in units of (l/min)/bar0.5)

An illustrative example: A sprinkler with an imperial K factor of 5.6 would give a flow rate of 15.0 US gpm with a pressure drop of 7.2 psi.

The flow rate is calculated from: 7.2 psi0.5 x 5.6 = 15.0 US gpm

A component could be used to model the flow and pressure loss through this sprinkler. For a given pressure drop across the sprinkler component, the flow rate is determined using a sprinkler K value of 5.6. The following are pressure drop / flow rate data points for such a sprinkler:

1.0 psi drop gives √(1.0) x 5.6 = 5.6 US gpm flow
4.0 psi drop gives √(4.0) x 5.6 = 11.2 US gpm flow
9.0 psi drop gives √(9.0) x 5.6 = 16.8 US gpm flow
16.0 psi drop gives √(16.0) x 5.6 = 22.4 US gpm flow

Alternatively, for a given flow rate through the sprinkler, the pressure loss can be calculated from the K value.

Note: Imperial & Metric sprinkler K factors are different. To convert from an Imperial sprinkler K factor to a Metric sprinkler K factor multiply by 14.4 approximately.

For standard type sprinkler heads the many design standards specify K-factors and minimum pressure requirements, which can be used for different Hazard classifications and design densities.

For information on how to apply the performance curve of the sprinkler using a Pipe Flow Expert Component object, please see 'How do I model a sprinkler system with Pipe Flow Expert?'

NOTE: In Pipe Flow Expert version 7 and later, the Spinkler K factor can be specified directly in the Component object and this one value can then be used to determine the flow versus pressure loss performance characteristic for the sprinkler nozzle.

Secure Online Payments And
Like Pipe Flow here: Pipe Flow Software: Piping design, Pressure drop calculator, Flow rate calculator, Pump head calculations, Pump selection software.  Copyright © Pipe Flow Software 1997-2019